A Simple Guide to Installing An Emergency Eyewash Station
Oct. 29, 2021
How to install an eyewash station?
So you have purchased an eyewash station (or stations) and are familiar with the all-important ANSI Z358.1 regulations - now it's time to install it. In this guide we will give you the basic installation instructions for wall-mounted and free-standing eyewash stations.
First things first: remove the packaging from your new eyewash station and ensure that you have all the necessary components (these should be listed in the manufacturer's instructions) and that they are undamaged.
You should also thoroughly rinse the inside and outside of the unit to ensure that any dust, dirt and debris that may have accumulated during storage is removed.
Finally, although the following instructions can be used as a general installation guide, all eyewash stations are different, so always read the manufacturer's instructions carefully.
Wall Mounted Eye Wash Wjh0359d
Installing a wall mounted eyewash station
What you will need.
Wall fastener anchors for 3/8" bolts
Bolts and washers ( 3/8 inch)
1 ¼" sliding fitting P-trap/drain connection
Place the appliance on the wall near the drain and water supply between 33" and 45" above the floor to comply with ANSI Z358.1. Hold the unit steady and mark the location of the mounting bolt holes on the wall. Remove the unit and install wall fastener anchors where you marked the wall, then secure the unit to the wall using 3/8" bolts.
Next, connect the tailpipe to the eyewash unit. Install the sanitary drain and P-trap so that it lines up with the eyewash unit and then connect to the tailpipe.
Finally, connect the supply line to the ball valve on the eyewash station. Turn on the water supply and test the unit for leaks, ensuring that the flow rate complies with ANSI regulations.
Emergency Eye Wash
Installing a freestanding eyewash station
You will need to prepare.
Floor fastener anchors
Bolts and washers
Position the unit with a minimum of 9" clearance between the left or rear wall and the centre of the drainage basin and a minimum of 11" clearance to the right wall. Secure the unit in place and mark the location of the floor mounting holes. Install the floor anchor in the appropriate position and bolt the unit to the floor.
Connect the drain hose to the 1 ¼" female tee. If not already installed, ensure beforehand that the drain is in a position to align with the female tee.
Finally, connect the water supply line to the ball valve on the eyewash unit. Turn on the water supply and ensure that the unit is discharging water at the ANSI approved rate and that there are no leaks.
RWD is one of the largest domestic laboratory and safety equipment manufacturers with a long history. Focus on the worktop, laboratory faucets, gas valve, fume extractor, pegboard, PP sink, Emergency shower and eye wash series products research & development and production, involving areas such as education, scientific research, pharmaceutical, medical, chemical, petrochemical, electronics, metallurgy, machinery, etc.
Let us help you find the best eyewash stations for your project. When you contact us, please provide your detailed requirements. That will help us give you a valid quotation.